Bi-Level Bowls Architectural Style Drinking Fountain (M-43B)
Architectural Style Fountain with Bi-Level Bowls for ADA
- Mounting: Pedestal
- Material: Cast Iron Pedestal , Cast Brass Bowl
- Pet Friendly: Available Option
- Freeze-Resistance: Available Option
- Activation: Push Button
- Style: Architectural Style
- Finish Available: Brown , Black , Green
- Health/Environomental: ADA Compliant , Green cUPC - Water Efficiency , Lead Free Fed. Law 111-380
Model M-43B features design simplicity. This unit has bi- level bowls to meet ADA requirements. The fountain includes stainless steel bubblers operated by separate pushbutton control. Standard model is seasonal, not freeze- resistant. Heavy duty construction ensures durability. Field serviceable components are easily accessible. Solid brass castings for bowl is Penny Vein powder coated and base/arm is finished in Chestnut Brown.
Drinking fountain shall be model M-43B. Unit shall be furnished with one fountain bowl mounted on the pedestal and one fountain bowl mounted on an arm.
Pedestal and arm shall be heavy duty iron castings and base of pedestal shall have four mounting holes. Pedestal and arm shall be furnished with a heavy grade of oil based enamel. Access cover shall be secured with vandal-resistant stainless steel screws.
Bowls shall be octagonal, powder coated, solid brass castings. Pet Fountain options provide a cast aluminum bowl with matte finish.
Valve shall be self-closing, pushbutton operated, incorporating a replaceable cartridge and requiring less than 5 pounds of force to operate. Valve shall includes an adjustable stream regulator controlling the water.
Bubblers shall be stainless steel and operate on a water pressure range of 30 - 105 psig.
All solid brass castings shall conform to ASTM standards B61 and B62. Unit is certified to ANSI A117.1, Public Law 111-380 (NO-LEAD), CHSC 116875 and NSF/ANSI 61, Section 9.
Lead Time: 2-4 weeks before shipment. This item is "Build to Order".
WARNING: Cancer and Reproductive Harm - www.P65Warnings.ca.gov
Learn More about this warning