3/4" Self-Closing Lever-Handle Jug FIller (M-ESH175)
3/4" Compression Jug Filler, Self-Closing Lever Handle, Side Inlet
- Mounting: Post Mounted
- Material: Cast Iron
- Bury Depth: 2 Ft , 3 Ft , 4 Ft , 5 Ft , 6 Ft
- Freeze-Resistance: Yes
- Inlet Size: 3/4"
- Activation: Lever
- Finish Available: Green or Black
- Hydrant Inlet Type: Female Threaded Side Inlet
3/4" FREEZE RESISTANT TRIMLINE POST HYDRANT WITH SHUT-OFF, HEAVY DUTY
Model M-ESH175 delivers year-round service outside or in unheated buildings. To provide freeze resistant functionality, the control valve is located below the frost line. The spring-loaded handle raises and lowers the internal supply line assembly, controlling the valve. The internal supply column is evacuated through drainage ports in the bottom and an integral internal shut-off valve ensures easy maintenance. This trimline design complements any setting. The hydrant must be operated fully "ON."
Hydrant shall be model M-ESH175. Unit shall be capable of year-round use in freezing weather and shall include an integral shut-off valve.
Unit shall extend below grade level so that centerline of supply inlet is positioned at or below frost line. Unit shall include an integral shut-off valve. Inlet shall have a threaded connection.
Water shall be gravity-evacuated from inner supply column when valve is shut off.
Valve shall be operated by lever handle spring-loaded for closure. Housing shall be cast aluminum, finished with a heavy grade of oil-based green enamel. Handle shall be an aluminum-bronze casting. All castings shall be manufactured in the USA and comply with ARRA standards, to include machining, assembly and painting.
Inner supply assembly shall incorporate solid-brass castings. All solid-brass castings shall conform to ASTM standards B61 and B62. Lead-free castings are used in all waterways.
Outer casings and inner supply line shall be galvanized-steel pipe.
Nozzle shall be solid brass casting, threaded for 3/4" hose connection.
WARNING: Cancer and Reproductive Harm - www.P65Warnings.ca.gov
Learn More about this warn