3/4" Dump Station Tower-Hydrant (M-275-RV)
3/4" Dump Station Tower-Hydrant, Side Union Inlet
- Mounting: Post Mounted
- Material: Cast Iron
- Bury Depth: 2 Ft , 3 Ft , 4 Ft , 5 Ft , 6 Ft
- Freeze-Resistance: Yes
- Inlet Size: 3/4"
- Activation: Lever
- Finish Available: Green
- Hydrant Inlet Type: Union Tail Side Inlet
3/4" FREEZE RESISTANT, SELF-CLOSING STOCK CAR HYDRANT
Model M-275-RV delivers year-round service outside or in unheated buildings. To provide freeze resistant functionality, the control valve is located below the frost line. Pulling down on the lever raises the internal supply-line assembly to the open position, and the self- closing spring lowers the internal supply-line assembly to the closed position. Constructed of heavy lead-free brass, premium-quality gray iron and steel, the M-275- RV is designed for trouble-free reliability and easy maintenance, and is the hydrant of choice for RV washdown areas and elevated railroad platforms.
Hydrant shall be model M-275-RV. Unit shall be capable of year-round use in freezing weather.
Unit shall extend below grade level so that centerline of supply inlet is positioned at or below frost line. Inlet shall have 3/4" NPT male connection.
Water shall be gravity-evacuated from inner supply column when valve is shut off.
Valve shall be lever operated. Lever shall be fabricated of one-piece iron casting finished with a heavy grade of oil-based green enamel. Stock, top, and base shall be fabricated of heavy, one-piece iron castings finished with a heavy grade of oil-based green enamel.
Inner supply assembly shall incorporate solid-brass castings. All solid brass castings shall conform to ASTM standards B61 and B62. Lead-free castings are used in all waterways.
Outer casing shall be black iron pipe, finished with a heavy grade of oil-based green enamel.
Hydrant shall consist of internal supply line and a surrounding outer casing pipe for protection of waterway.
Nozzle shall be solid brass casting, threaded for 3/4” NPS hose connection.
Self-coiling hose is provided with the hydrant.
WARNING: Cancer and Reproductive Harm - www.P65Warnings.ca.gov
Learn More about this warn